Status changed: Draft to Pending.
Attend site as requested to commission and to find communication on a fault between outdoor and
indoor units and commission the VRV system . dates on site: 28/29/30 and 31st of July.
NOTE: On the Bedroom 3 the cable connected to the fan coil wasn’t connect to the BC box, after
investigation a second cable was found below the fan coil and communicate on was established,
so the system could be commissioned.